Customized Water Cooled Low Temperature Reciprocating Chiller
|FOB Price:||US $15,000-50,000 / Piece|
|Min. Order:||1 Piece|
|Min. Order||FOB Price|
|1 Piece||US $15,000-50,000/ Piece|
|Production Capacity:||100 Units Per Month|
|Payment Terms:||T/T, Western Union, Paypal, Money Gram|
- Model NO.: AYD-25WDL
- Cooling Method: Water-cooled
- Selected Voltage: 380V/50HZ
- Noise Level: Ordinary
- Application Machine: Machining Center
- Condition: New
- Input Power: 12.55kw
- Cooling Tower Flow: 65m3/H
- Trademark: Anyda
- Specification: 1700*1100*1800mm
- HS Code: 8418692090
- Type: Water-Cooled
- Unit Structure: Integral
- Compressor Number: 1
- Application Fields: Low Temperature
- Certification: CE
- Cooling Capacity: 14kw
- Outlet Temp: -45c
- Cold Water Flow: 50m3/H
- Transport Package: Wooden Case
- Origin: China
Anyda water cooled low temperature glycol chillers are equipped with compressor and pump overload protector, phase shortage and reversal alarm, anti - freeze thermostat, pressure gauge etc. They feature excellent performance and a long life span. This series of working flow is based on the basic principle of heat exchange. It is applicable to the industry that requires flow of precisely controlled chilled water, and considered as indispensable equipment for modern industry.
Applied Machinery: Cooling system of oil temperature, ultrasonic, high frequency machinery, injection molding machinery, blow molding machinery.
SPECIFICATIONS FOR WATER COOLED LOW TEMP GLYCOL CHILLER
Shell and Tubes
Shell and Tubes
1.How does a chiller system work?
Chiller has two circulation,one is process water circulation,the other is refrigerant gas circulation.Heat picked up from the process.Heat transfers to refrigerant circulation.Heat is remove to air or water.
2.How to calculate cooling capacity for chillers
Cooling Capacity(kw)= Flow Rate(m3/h)*Temp Change(T1-t2)/0.86
Heat Load= C(specific heat)* M(quality output per hour )*Temp Change(T1-T2)
3.Types of chiller system?
Air Cooled Chiller and Water Cooled Chiller.Water cooled chiller needs a separated cooling tower and has a higher efficiency,but less easier than air cooled.
4.Cooling capacity unit conversion?
1 kcal/h = 1.163W,1 W = 0.8598 kcal/h;
1 Btu/h = 0.2931W,1 W = 3.412 Btu/h;
1 USRT = 3.517 kW,1 kW = 0.28434 USRT;
1 kcal/h = 3.968 Btu/h,1 Btu/h = 0.252 kcal/h;
1 USRT = 3024 kcal/h,10000 kcal/h = 3.3069 USRT;
Step 1: Keep Tubes Clean
Step 2: Ensure a Leak-free Unit
Step 3: Sustain Proper Water Treatment(prevent scale, corrosion)
Step 4: Analyze Oil and Refrigerant
1.Reply your inquiry within 12 working hrs.
2.Strong R&D team,more than 15 years of manufacturing chiller experience. OEM&ODM is welcomed.
3.Direct factory,offer customer competitive price with high quality chiller.
4.Strict quality control system,professional QC team.